Ultrafit SWR premium quality UPVC material ensure a long lasting performance. Ultrafit SWR with world class seals are used in building drainage of residential, commercial, industrial & public complexes.
Pipes: 40 to 160 mm nominal diameter.
Rubber Ring Joint: 75, 90, 110 & 160 mm
Solvent Joint: 40 to 160 mm
Lighter but strong
Compatible with other drainage products
Easy to install with low assembly force
World-class seals ensure longterm sealing performance against leakage
Inside & outside building drainage systems including ventilation
It is imperative to mark the pipe from all sides so that pipe is cut with the help of a Hand Saw. It should be a right angle cut from all the sides. The cut piece should not be with burr on edges.
Do not cut slant/ unevenly.
(This step is required when pipe cutting is done from3 mtr pipe to any required length during installation)After cutting, the pipe needs to be chamfered from the outer sides. It is advisable to provide an approximately2 mm wide,150 chamfer on spigot end.
Do not proceed with installation of pipe without chamfering.
Deburring and Ridge Removal
Remove all the burrs and ridges accumulated on the inner as well as the outer edges of the pipe with the help of a deburring knife, file or abrasive paper.
Do not proceed with the installation of pipe without deburring.
Before applying solvent cement, insert the pipe end into the socket of the next pipe or fitting to check that interference occurs at about 1/3 to 2/3 of the socket depth.
Do not apply solvent cement without dryfit test.
Thoroughly clean the pipe with dry cloth where the solvent cement is going to be applied to avoid dust, dirt, oil, moisture and other foreign materials during the installation process.
Do not join the pipes without cleaning the pipe ends.
Application of Solvent Cement
Mark the pipe length to be inserted for jointing. Apply a liberal coat of solvent cement with the help of the brush on the marked surface.
Do not apply excess solvent cement on the pipe and do not use solvent cement by hand.
Push the pipe inside the fitting / pipe so that it goes inside equally from all the sides. Wipe off excess solvent cement that comes out from all the edges. Hold the joint for one to two minutes so that the jointing is perfect.
Do not use a hammer or half push the pipe.
Installation and Commissioning
Pipe line should be installed in proper alignment & along with necessary clamps.
Pressure testing may be carried out after a curing period of 24 hrs.
Avoid loose joints & misalignment.
Pressure testing should not be done before 24 hrs of curing.